Introduction of 0.6/1kV PVC Insulated Overhead Cable
For single core PVC insulated or covered overhead cable without messenger or neutral conductor, the phase conductor may be AAC or AAAC or ACSR or Copper.
For more than one core PVC insulated overhead cable with or without messenger or neutral conductor and with or without street lighting conductor, the phase conductor and street lighting conductor are AAC with PVC insulation, and the messenger or neutral conductor is AAAC or ACSR with or without PVC insulation.
Operating Characteristic of 0.6/1kV PVC Insulated Overhead Cable
Rated voltage: 0.6/1kV;
Max. permissible continuous operating temperature of conductor with PVC insulation: 70°C;
Max. temperature of conductor during short-circuit (5s max. duration) shall not exceed: 160°C;
The ambient temperature under installation should not be lower than: -20°C.
The bending radius of cable is recommended as following:
When the diameter of cable is less than 25mm: not less than 4 times of the diameter of cable;
When the diameter of cable is not less than 25mm: not less than 6 times of the diameter of cable;
When the cable is used in alternative current system, the rated voltage of cable should be at least equal to the rated voltage of system; when the cable is used in direct current system, the rated voltage of system should not greater than 1.5 times of the rated voltage of the cable.
Application of 0.6/1kV PVC Insulated Overhead Cable
PVC insulated overhead cable as a new-type overhead cable is used for overhead electric power transmission, extensively used in rebuilding of urban and forest region electrified wire netting. It improves the safety and reliance of electrified wire netting.